UL Warns of Ground Rods with Unauthorized UL Marks
NORTHBROOK, Ill., April 14, 2011 /PRNewswire/ — Underwriters Laboratories (UL) is notifying Authorities Having Jurisdiction (AHJs), electrical contractors, electricians and retailers that the ground rods identified below bear unauthorized UL Marks for the U.S. and Canada. These products have not been evaluated by UL to the applicable Standard for Safety for the U.S. and Canada and are not authorized to bear the UL Mark.
Name of Product: Ground Rod, Model 834 cUL US LISTED 4X41
Number of Units: Unknown
Date of Manufacture: Unknown
Defect: The thickness of the copper plating for these ground rods does not comply with U.S. and Canadian Standards for Safety. It is unknown whether the ground rods are suitable to ensure an adequate ground path.
Identification: The ground rods are 3/4 inch in diameter and eight feet long. The ground rods are marked on one end of the rod with the following information: 834 cUL US LISTED 4X41
Photos of the Ground Rod: Photos available at http://www.ul.com/global/eng/pages/corporate/newsroom/publicnotices/
Distributed By: The ground rods may have been sold by electrical distributors throughout the United States.
UL is a premier global safety science company with more than 100 years of proven history. Employing more than 6800 professionals in over 96 countries, UL is evolving the future of safety with five distinct business units – Product Safety, Environment, Life & Health, Verification and University-to meet the expanding needs of customers and the global public. Additional information about UL can be found at UL.com or Safetyathome.com.